Download Sizing Guide:
Voltage Drop for 000 B&S Cable:
To calculate the voltage drop of 000 B&S copper cable, use the following formula:
Voltage Drop = Length x Current x 0.017 Area (83.19)
Length = Total length of cable in metres.
Current = Current draw (amps) through the cable.
Area = Cross sectional area of the copper (in this case 83.19mm²)
Formula only applies to copper at 25°C, voltage drop increases with both ambient and cable temperature, at approx 0.4% per °C.
0.017 - This multiplication factor only applies to copper
Example for 000 B&S:
How much voltage drop over 10m of 000 B&S with a current draw of 335A?
- 10m x 335A x 0.017 = 56.95
Divide this by 83.19 (cross sectional area of 000 B&S - mm²)
You will have a drop of approximatley 0.68 Volts over the 10m length